The cooling issue that prompted us to shut down Summit has been identified and is being rectified. We expect to be able to bring Summit back into production later today.
Recently, a maintenance issue was discovered in the HPCF affecting the reliability and longevity of the cooling system. We have been planning an outage to coincide with the 1 August planned maintenance to address this issue, but we have been conducting daily maintenance to prevent the issue from getting worse in the mean time. This morning, a portion of the cooling system was left in a maintenance state. As a result, all water was allowed to drain from the cooling tower, and the facility began to overheat.
We are restoring the cooling system to its production state, after which we will be bringing Summit back up and into production; however, be advised that we will be taking an extended outage starting 1 August to fully address these related issues. (The maintenance is currently planned to last 3 days.)
Thank you for your understanding while we address this issue. If you have any questions or concerns, please contact email@example.com